NAMEoneac - Driver for oneac UPS equipment
NOTEThis man page only documents the hardware-specific features of the oneac driver. For information about the core driver, see nutupsdrv(8).
SUPPORTED HARDWAREThis driver supports Oneac EG and ON UPS equipment with the Advanced Interface. If your UPS is equipped with the Basic Interface card, use the genericups driver.
EXTRA ARGUMENTSThis driver supports the following optional settings in the ups.conf(5) file: testtime=num Change battery test time from the 2 minute default.
INSTANT COMMANDSThis driver supports the following Instant Commands. reset.input.minmax Reset the minimum and maximum input line voltage values seen since the last reset or power on. test.battery.start Start a battery test. The default time is 2 minutes. This time can be set in the ups.conf file. See testime above. test.battery.stop Stops a battery test that is in progress. test.failure.start Starts a 15 second long simulation of an input power failure.
AUTHOREric Lawson <firstname.lastname@example.org>
SEE ALSOThe core driver: nutupsdrv(8) Internet resources: The NUT (Network UPS Tools) home page: //www.networkupstools.org/ ONEAC(8)